This is a group of goods necessary for the assembly of devices or their additional protection. We have also described here the type of buses that are used in devices manufactured by MIKRONIKA. The strips are designed for analog and communication channels. There are also variants where some of the channels are intended for the communication part and the other for the analog one. 
COLOR - not recommended for use | COLOR - module/device manufactured
The LWA-002 / LWK-002 analog/communication input strip is designed to introduce two-wire connections of analog or communication signals from the object to the object controller, while protecting the controller inputs against electrostatic discharges, surge disturbances and fast electrical transients. The strip is adapted to be used in industrial automation, measurement and control installations.
It comes in 3 configurations:
The LWB-002 binary input strip is designed to introduce binary signal connections from the object to the object or communication controller, while protecting the controller inputs against electrostatic discharges, surge disturbances and fast electrical transients. The strip is adapted to be used in industrial automation, measurement and control installations. 
The LWS-002 control output strip is designed to output mutually galvanically separated, contact, two-wire control signals from the object controller to object devices. The strip is adapted to be used in industrial automation, measurement and control installations. 
The OGP-001 two-stage surge arrester is designed to eliminate and limit the effects of strong interference in electrical installations. The electrical parameters of the arrester allow to increase the resistance to surge disturbances of the protected devices up to level 4 (according to the PN-EN 61000-4-5 standard). The basic version is based on the varistor technique. However, it is possible to change the parameters of the limiter by connecting two different or similar sections, consisting of spark gaps, varistors or protective diodes. The OGP-001 can be used in single- and three-phase systems (3x OGP-001). The housing used allows mounting on a 35 mm DIN rail. 
The bus used is assigned to a specific family of devices. As a result, devices/modules are prepared to work in specific configurations. Some of them are equipped with several buses, which makes them more universal. The use of a given bus forces the device/module to be mounted in specific types of enclosures.
MIKRONIKA devices use the following buses: